SECTION – I
YAPP INDIA AUTOMOTIVE SYSTEMS PVT LTD.
Plot No. A-3/A, Chakan Industrial Area, Phase II,
Village Khalumbre, Taluka Khed, Chakan,
Off. Chakan-Talegaon Road, District Pune,
Maharashtra – 410 501. India.
This document covers the write up of water based fire protection systems for the Automotive Fuel Tanks Factory.
All the systems are designed in accordance with codes & standards in compliance with the requirements acceptable to TAC / nominated agencies of the insurance companies.
SECTION – II
The design & installation of water based fire protection Systems complies with the guidelines /codes / standards / rules published by TAC / NBC/NFPA. The following standards / codes are followed in particular:
- TARIFF ADVISORY COMMITTEE OF INDIA (TAC):
– FIRE PROTECTION MANUAL
– SPRINKLER REGULATIONS
- NATIONAL BUILDING CODE OF INDIA (FIRE AND LIFE SAFETY)
- NATIONAL FIRE PROTECTION ASSOCIATION of USA (NFPA):
– NFPA 13 (Standard for Sprinkler Installation)
– NPFA 15 (Standard for Water Spray Fixed Systems for Fire Protection)
SECTION – III
FIRE PUMPS DETAILS
|1||Main Fire Pump(Centrifugal) Motor Driven Working Pump||137 M3/Hr.||70 Mtrs||2900||1 No.|
|2||Jockey Pump (Centrifugal) Motor Driven||10.8M3/Hr.||70 Mtrs||2900||1 No.|
|3||Main Fire Pump(Centrifugal) Engine Driven Stand By Pump||137 M3/Hr.||70 Mtrs||1400||1 No.|
FIRE HYDRANT SYSTEMS
Fire Hydrant systems are installed as one piping networks. We have installed total 10 Nos. of hydrant along the perimeter of YAPP ZOOM factory as well as at staircase along with Hose, Branch pipe & Nozzle.These hydrant accessories kept in Hose cabinet near to each hydrant outlet.
FIRE SPRINKLER SYSTEMS
We have installed 704 nos. of sprinklers pendent type standard response in yapp zoom factory as per client/std. code requirements along with necessary accessories.
FIRE ALARM SYSTEMS
We have installed Addressable Fire Alarm system at YAPP ZOOM. Fire Alarm System consists of detector in various zones which checks/detect any abnormal change in smoke, heat level. Theses detector then give signal back to the fire alarm panel which then actuate the corresponding output devices (Hooters & Relays) as programmed to take appropriate extinguishing measures.
SECTION – IV
FIRE AUDIT & AMC
We are currently undertaking 2 times fire audit and 4 times AMC in a year for installed firefighting systems in YAPP ZOOM Factory.